TRANE ECONOMIZER WIRING DIAGRAM
INSTALLER'S GUIDE - trane
PDF fileEconomizer enthalpy changeover is field selectable to 4 points. See the following table for potentiometer settings. The selection is made on the ECA. unit wiring diagram to make the low voltage connections. Figure 2 FIYCOPO- Powered Convenience Outlet Powered Option - Figure 2
Installation,Operation, and Maintenance - trane
PDF fileTrane believes that responsible refrigerant practices are important to the environment, our customers, injury field wiring MUST be performed by qualified personnel. Factory Installed Economizer Temperature Limit Switch Usage for Gas Heat Units
63-2596—09 - W7212, W7213, W7214 Economizer Logic Modules
PDF fileW7212, W7213, W7214 ECONOMIZER LOGIC MODULES 5 63-2596—09 Mount the CO2 sensor according to the manufacturer specifications. If not available, use the following guidelines: 1. Mount sensor in an area with unobstructed air circulation. 2. Connect it to the AQ and AQ1 terminals of the W7212 (see Wiring section for details). 3.
HVAC Economizers 101 Section #6 U T R i Mftf SiM
PDF fileTrane Voyager / Economizer Features and Operations-Horizontal • The horizontal economizer contains the same features as the down flow economizer with the exception of barometric relief. • Motorized outside air dampers manually set outdoor air dampers and provide up to 50% outside air Once setdampers and provide up to 50% outside air. Once set,
User guide - Trane
PDF fileas a guide to the installation, start-up, operation and periodic ECA Economizer Module EDC Evaporator Defrost Control EM HEAT Emergency Heat The following wiring diagram applies for units equipped with Reliatelcontroller with the TCI communication interface.
JADE Economizer Module - Honeywell
PDF fileJADE ™ Economizer Module (MODEL W7220) This document describes wiring, power up, basic troubleshooting, and common installation issues for the JADE™ Economizer Module (Model W7220). For further information on mounting and operation, refer to Honeywell document 63-2700. BEFORE INSTALLATION Review the following before installing the The W7220
ReliaTel Microprocessor Controls 3 to 10 ton Convertible
PDF file3 to 10 ton Convertible and 12½ to 50 ton Dedicated Packaged Rooftops 3 to 10 ton cooling only and gas electric convertible packaged units can be built with either electromechanical or ReliaTel™ controls. 12½ to 50 ton units are built with ReliaTel controls only.
Installation Operation Maintenance - Amick Racing
PDF fileInstallation Operation Maintenance Packaged Gas/Electric YC-IOM-13 18-EB60D15 December 2004 C = Downflow Economizer and Oversized Motor F = Trane Communications Interface(TCI) trical wiring, fan belts, thermal insulation, various fasteners and bushings.
Trane TSC060ED Installation, Operation And Maintenance Manual
View and Download Trane TSC060ED installation, operation and maintenance manual online. Nominal Gross Economizer, Reference Enthalpy Trane Communications Interface 0-100% without Barometric Relief LonTalk® Communications Interface Cooling Capacity (MBh) Maintenance Final Process Wiring Diagram Numbers (from unit control panel)
Trane economizer wiring - HVAC-Talk: Heating, Air
Trane economizer wiring installing field kit economizer on 18 to package unit air on the side. comparative empathy is to be installed in return air duct with field wiring. If i run the wires on the inside cant see a good way around the bypass doors.