HVAC - How to Size and Design Ducts - CED Engineering PDF fileHVAC – HOW TO SIZE AND DESIGN DUCTS . Air flow problems have plagued the HVAC industry for years. No matter how much money means a duct size can be recalculated for a new air velocity using the simple equation: V 2 = (V 1 * A 1)/A 2 where V is velocity and A is Area . 2. STANDARD MECHANICAL ABBREVIATIONS DUCT DETAILS (LOW PDF fileflex duct see spec for type see schedule for size dampers section plan section plan supply diffuser hard connection sidewall supply grille connection conical tee low loss lateral tee conical lateral r=1-1/2d r= l=d1-d2 r elbow y-branch bell mouth reducer medium pressure ductwork branch fittings standard mechanical abbreviations without with Manual D – HVAC Duct Design and Layout Drawing Service Our Basic Manual D, is the conventional HVAC Manual D with a basic 2D Drawing. If you would like a little more detail, upgrade to our Premium Manual D service and get a 3D render image of your Duct Design in addition to the official Basic Manual D. HVAC Ducting Principles and Fundamentals PDF file3. High Velocity Duct Systems: High-velocity (HV) duct systems are characterized by air velocities in the range of 2500 to 3500 fpm. Low-velocity ductwork design is very important for energy efficiency in air distribution systems. Low-velocity design will lead to larger duct sizes, but it Arlan Burdick IBACOS, Inc. - NREL PDF fileBasics and Duct Design Arlan Burdick IBACOS, Inc. December 2011. NOTICE . This report was prepared as an account of work sponsored by an agency of the HVAC design flow... 2 Figure 2. General steps for air distribution design (PDF) HVAC Design & Drafting per ASHRAE | Mohamed Academia is a platform for academics to share research papers.