3 WAY DIVERTING VALVE PIPING DIAGRAM
60-2129 - V5013B,C,F Three-Way Mixing and Diverting Valves
PDF fileV5013B,C,F THREE-WAY MIXING AND DIVERTING VALVES 5 60-2129—4 Fig. 7. Typical zone hookup of V5013C diverting valve used to control flow through coil. Valve Installation Threaded Valve bodies Line up the pipes squarely with the valve at each end. If the pipes are forced into the valve, the body may become twisted and improper seating will result.
Learn More About HVAC Three-Way Valves | Industrial Controls
As in two-way valves, if the three-way valve selected is less than line size, don’t forget the FP factor. Resize the valve applying the FP factor to find the new CV. For three-way valves used in chilled water-hot water, summer-winter changeover, mixing two-position or diverting, use a line size valve. This is a low D P application.
71543-00001 3-Way Diverting Ball Valves Instruction Manual
PDF file3-Way Diverting Ball Valves 3-Way Diverting Ball Valves Three-way valve with chrome plated brass ball and nickel plated stem and NPT female ends Technical Data Service chilled or hot water, 60% glycol 3. Blow out all piping and thoroughly clean before valve installation. 4.
Characterized Control Valves (CCV) Installation Instructions
PDF file2. Install valve with the proper ports as inlets and outlets. See drawings on page 1. Check that inlet and outlet of 2-way valves are correct; check that the “A”, “B”, and “AB” ports of three-way valves are piped correctly. Flow direction arrows must be correct. 3. Blow out all piping and thoroughly clean before valve
Three-Way Ball Valves: A Great Diversion
The L-Port, which also goes by “diverting valve” is the most commonly used version of the three-way ball valve. Depending on the piping arrangement, turning the handle 90 degrees will divert the materials being pumped from one pipe to another. Or in other applications, you can switch from one pump to another, with a common outlet.
Three Way mixing valves - HVAC/R engineering - Eng-Tips
As I understand it, functionally there is no difference whether you use the mixing valve or diverting valve; however, I have seen more often than not, the mixing valve in these three-way valve applications (where the valve is in the return piping vs. the supply side of the coil where it would be a diverting valve).
B332L, 3-Way Diverting Ball Valve
PDF fileB332L, 3-Way Diverting Ball Valve Chrome Plated Brass Ball and Nickel Plated Brass Stem 800-543-9038 USA 866-805-7089 CANADA 203-791-8396 LATIN AMERICA / CARIBBEAN
Bypass Application Using Three-Way Valves
PDF file(two inlets, one outlet) and diverting valves (one inlet, two outlets). The type of three-way valve selected will determine its location in the system. S R Outlet N.O. N.C. Inlet Outlet Coil Figure 1: Diverting Valve in a Bypass Application Piped N.C. to Coil Diverting valves in
CA-27 - Schneider Electric
PDF fileCA-27 Three-Way Valves Application Information. Figure-11 Three-Way Diverting Type Valve (Pipe Incorrectly for Mixing Service). be a “by-pass” application of a three-way valve. Naturally, the piping method chosen will depend on what type of valve body is specified.
Three-way Mixing Valve Installation Guide
PDF fileThree-way Mixing Valve Installation Guide 3 Installation Refer to the following installation instructions to properly install the Uponor Three-way Mixing Valve. 1. The valve body can install in any position and orientation. Install the power connections over the supply port to ensure proper flow direction (see Figure 3). 2. Before installing